EPCO's UV resistant Porcelain Lamp Holders are ideal for Commercial, Industrial, Residential and Agricultural Lighting Applications.
- UL Listed. File #E236781.
- Nickel-plated brass screw shell will not corrode.
- For Commercial, Industrial, Residential and Agricultural Lighting Applications.
- Fits 3.25” or 4” outlet box.
- UV resistant Lamp Holders will not fade or discolor.
- Optional Plastic and Metal Safety Cages fit all Lamp Holders.
- Includes corrosion resistant mounting screws.
- Meets the requirements of the 2023 National Electrical Code: Articles 410.1, 410.50, 410.51, 410.52, 410.80(A)(B) and 410.122.
NOTE: Lamp Holders are ONLY sold in case quantities of 48 per Carton.
Installing Lamp Holders for Poultry Farming Applications
EPCO recommends using only Porcelain Lamp Holder(s) for poultry farming applications. The lamp holder must be installed in a manner that will not permit dust or moisture to enter the junction box. In addition, the porcelain lamp holder must be mounted vertically with the lamp positioned below the lamp holder on a water-tight, dust-tight non-metallic junction box with an effective gasket between the junction box and the lamp holder as shown in the photo to the right.
Use the part numbers below to facilitate and complete the installation as shown.
|Catalog Number||UPC Number||Description||Order Unit||Unit Qty||Unit Pkg||Units/ Case||TL Case Qty||Min Order Qty||MM Req||Ship Wt (Lbs)|
|15045||15045||12 Cubic Inch Junction Box: 1/2" and 3/4" Knockouts||EA||1||BX||12||12||12||Yes||6|
|15046||15046||12 Cubic Inch Junction Box: 1/2" Knockouts||EA||1||BX||12||12||12||Yes||6|
|15047||15047||12 Cubic Inch Junction Box: 3/4" Knockouts||EA||1||BX||12||12||12||Yes||6|
|15049||15049||19 Cubic Inch Junction Box: 3/4" Knockouts||EA||1||BX||12||12||12||Yes||6|
|15246||15246||12 Cubic Inch SPIDERBOX Junction Box: 1/2" Knockouts||EA||1||BX||12||12||12||Yes||6|
|15247||15247||12 Cubic Inch SPIDERBOX Junction Box: 3/4" Knockouts||EA||1||BX||12||12||12||Yes||6|
|16500||16500||Porcelain Lamp Holder: Keyless, 4-Terminal||EA||1||BX||48||48||48||Yes||33|
|16502||16502||Porcelain Lamp Holder: Pull Chain||EA||1||BX||48||48||48||Yes||35|
|16514||16514||Porcelain Lamp Holder: Pull Chain and 15 AMP Receptacle||EA||1||BX||48||48||48||Yes||40|
- Junction boxes include screws to affix the lamp holder to the junction box.
- Plastic Lamp Holders are NOT suitable for this application and will VOID the Warranty!
WARNING: EPCO Lamp Holders Must Be Installed in Accordance with the following 2017 National Electric Code Articles that state:
Where the wiring method is conduit, tubing, Type AC cable, or other cables, a box or conduit body shall be installed at each conductor splice point, outlet point, switch point, junction point, termination point, or pull point, unless otherwise permitted in NEC 300.15(A) through (L).
In addition, Article 502.130(2)(3) requires luminaires for fixed lighting shall be provided with enclosures that are dust tight or otherwise identified for the location as well as protected from physical damage by suitable guards for areas described in Article 547.1(A).
If the Contractor has taken care to install the porcelain lamp holder(s) in the proper manner as described and shown above and believes the lamp holder is defective, and wants to file a warranty claim, EPCO will require an “Affidavit of Inspection” from the Contractors local Electrical Inspector to validate the defined installation procedure. This document is intended to protect the integrity of the company (EPCO) and the Distributor.