Product SpecsDescriptionThe Landscape SplicePost for outdoor luminaires is different from any other "hollow pipe" style landscape lightpost on the market. It features an internal wiring compartment/junction box, rated for 19 cubic inches that easily accommodates two (2) 20 AMP circuits. The Landscape SplicePost allows the installer to make a proper ground connection to safeguard people and property from electric shock hazards. The Landscape SplicePost is UL Listed as a "Luminaire Fixture Fitting," suitable for use in wet locations. Meets the requirements of the 2017 National Electrical Code: Articles 314.15, 314.16(A)(2) and 314.17(B). The Landscape SplicePost features a Separator Disk™ and SpliceCap™ that creates an integral "junction box" suitable for splicing. The PVC SpliceCap is non-metallic and suitable for the majority of outdoor luminaires on the market. Replaces EMT, conduit connectors and weatherproof boxes. Ready to install. No assembly required. Corrosion and UV resistant. 100% shatter resistant. Part Numbers Landscape SplicePost: BlackCatalog Number: LSPBUPC Number: 17200 More Details Order Unit: EAUnit Quantity: 1Unit Package: BXUnit Per Case: 9Total Case Quantity: 9Min. Order Quantity: 9Ship Weight: 21.00lbs.MM Req.: Yes Landscape SplicePost Replacement Cap: BlackCatalog Number: 17230UPC Number: 17230 More Details Order Unit: EAUnit Quantity: 1Unit Package: BXUnit Per Case: 12Total Case Quantity: 12Min. Order Quantity: 12Ship Weight: 1.00lbs.MM Req.: Yes Dimensions Other Views A. SpliceCap accommodates a 1/2" trade size conduit nipple. B. NEC Article 314.17 – Conductors entering boxes, conduit bodies or fittings shall be protected from abrasion and shall comply with 314.17(B). C. …Where raceway or cable is installed with metal boxes or conduit bodies, the raceway or cable shall be secured to such boxes and conduit bodies. D. NEC Article 314.4 – All metal boxes shall be grounded and bonded in accordance with Parts I, IV, V, VI, VII, and X of Article 250 as applicable, except as permitted in 250.112(I). E. Replaces EMT, conduit connectors and weatherproof boxes. F. NEC Article 314.15 …boxes, conduit bodies and fittings installed in wet locations shall be listed for use in wet locations. NEC Article 314.16(A)(2) – Boxes 1650 cm³ (100 in.³) or less, other than those described in Table 314.16(A), and non-metallic boxes shall be durably and legibly marked by the manufacturer with their volume. The Landscape SplicePost is shatter resistant to denting or cracking typically caused by landscape maintenance equipment. It is also corrosion and UV resistant and impervious to changing environmental conditions. G. Uni-Stabilizer™ features unique concave stabilizing blades that allows ground material to be easily packed around the Landscape SplicePost for fast, easy and secure installation.The Uni-Stabilizer helps minimize the Landscape SplicePost's movement typically caused by ground freezing and thawing. H. When wiring multiple luminaires in series, the Landscape SplicePost's angled bottom allows UF Cable or Conduit to easily enter at different depths to eliminate cable congestion. A. SpliceCap compartment fully encloses and protects the circuit conductors from moisture, dirt and abrasion. B. The SpliceCap's 19 cubic inch box volume can house two 20 AMP circuit conductors. C. Raised "Grips" simplify installation and removal of the SpliceCap. D. Eight (8) internal "Stops" seat and firmly hold the Separator Disk™ in place when the SpliceCap is positioned on the PVC Pipe. E. UF Connector secures the incoming supply line cable to the Separator Disk. F. Separator Disk with attached Ground Wire. Use with non-grounded metallic luminaires to make a safe ground connection. G. Incoming supply line cable.